LEX PRODUCTS POWERGATE OUTPUT PANEL - SPECIFICATION BOILERPLATE 3.3.6.
The lower chamber shall have individual cable holes to restrict access and reducing the possibility of theft
. 3.3.7. Cables shall enter and exit the wiring chamber via access holes specifically designed for conductors and shall be provided with a bushing or shall be formed so that there are no sharp edges with which conductor insulation may come in contact. 3.3.8. The cable access holes shall have a hinged door to securely cover the cable access holes when the temporary cables are not installed. 18.104.22.168 The cable entry cover shall open inwards so that the connection chamber is fully enclosed and protected, even when the panel is in use. 3.3.9. The output panel shall have a removable cable entry lock plate to reduce risk of cable tampering. The cable entry lock plate secures the hinged bottom access door in place when the panel is not in use. 3.3.10. The output panel shall have an outer, hinged access door restricting access to wiring chamber for safety and security. 3.3.11. The outer access door shall have a pad lockable handle, preventing unauthorized entry. 3.3.12. [ SPECIFY EITHER: No trap key provision OR panel shall have one (1) trap key provision on main panel door. 22.214.171.124. Output Panel with trap key provision shall come with 4X NEMA Rated, UL Listed hole seal. 126.96.36.199. Output Panel shall maintain cULus Listing with hole seal in place or trap key installed per installation instructions. 3.4. 1200 and 1600 Amp Models 3.4.1. The output panel shall have an enclosure manufactured of [ SPECIFY EITHER: 14 gauge galvanized steel painted ANSI 61 gray OR 316 stainless steel OR 304 stainless steel]. 3.4.2. The output panel enclosure dimensions shall not exceed 35 wide x 56 high x 30 deep. 3.4.3. The output panel shall include four (4) feet with anchoring holes for pad mounting. 3.4.4. The output panel shall be divided into an upper termination chamber and a lower wiring chamber.Previous Page