LEX PRODUCTS POWERGATE OUTPUT PANEL - SPECIFICATION BOILERPLATE 1. GENERAL 1.1. PowerGATE Power output panels shall provide a safe, convenient and economical way to connect a load bank to a generator for testing. 1.2. PowerGATE Power output panels shall be available in rating configurations of 400 Amp, 800 Amp, 1200 Amp and 1600 Amp service. PowerGATE Power Output Panels shall be cULus Listed to UL 891 for switchboards. 2. COMPLIANCE 2.1. The 400 Amp - 1600 Amp power output panels must be Listed to UL 891. 2.2. UL and cUL Listed labels shall be secured to the panel. 2.3. The output panels are to be fully tested by a Nationally Recognized Testing Laboratory (NRTL), to meet UL 891 requirements. Built to the standard shall not be accepted. 2.4. All power output panels shall be Type 3R compliant and the Type 3R rating shall be maintained with the temporary cables engaged. 3. MECHANICAL 3.1. All power output panels shall be constructed of aluminum, mild steel or Stainless Steel. 3.2. Connections shall be arranged so that cables drape downward when connected. 3.3. 200 - 800 Amp Models 3.3.1. The power output panel shall have an enclosure manufactured of [ SPECIFY EITHER: aluminum and painted ANSI 61 gray with a textured finish OR Grade 316 stainless steel OR Grade 304 stainless steel]. 3.3.2. The power output panel enclosure dimensions are to be 24" wide x 32 high x 11.5 deep.
3.3.3. The power output panel shall include
four (4) welded mounting tabs for wall mounting
. 3.3.4. The power output panel shall be divided into an upper termination chamber and a lower wiring chamber.
The upper termination chamber shall have a dead front panel covering all exposed electrical parts